The Notifier MMX-101 is a compact unit that can be install in a single gang junction box behind the monitored unit. Also, its small size and weight allow it to be install without rigid mounting. Besides, Notifier MMX-101 Monitor Modules provide a two-wire; Style B (Class B) initiating circuit for normally-open (N.O.) contact fire alarm and supervisory devices.
In general, all wiring must be install using the proper wire size and be in compliance with the National Electrical Code; all applicable local codes, and requirements of the authority having jurisdiction.
- Connect the red and black wires to the positive (+) as well as negative (–) loop power leads of the control panel signaling line circuit (SLC).
- Connect the violet (+) and yellow (–) wires to a two-wire, normally-open initiating device.
- Set the module address in accordance with system requirements. A given module can be set to any address between 00 and 99.
- Install the module in the desired mounting location.