The System Sensor RTS451 is an automatic fire detector accessory designed to test a remotely located detector. Consult detector installation instructions for additional information.
A test coil is required only for use with DH400/ DH500 models and requires ordering of part #COIL.
Consult the appropriate detector installation instructions for the applicable wiring diagram. Furthermore, the RTS451 mounts to a single gang box (21 /2” minimum depth), or directly to the wall or ceiling.
Place and also hold the painted side of the magnet to the RTS451 on the right or left side of the LED.
With the magnet in place some time will elapse (40 sec. maximum) depending on the detector type, before the alarm indicating LED will light.
Gently insert a 1 /8″ maximum diameter tool into the hole until it stops and LED turns off. Additionally, the RTS451 is capable of resetting only certain System Sensor models of detectors. Refer to detector installation instructions for additional information.
Features / Specifications
- Total Current: 105 mA max
- Test Switch: 10 VA @ 32 VDC
- Reset Switch: 10 VA @ 32 VDC
- Alarm Response Time: 40 sec. max.
- Temperature: –10°C to 60°C (14°F to 140°F)
- Humidity: 95% RH Non-condensing