The Firefighters ADT-FPJ Phone Jack mounts to a single-gang electrical box (4 x 2-1/8 x 2-1/2) or, when an addressable mini monitor module is install with it, a deep single-gang electrical box (4″ x 2-1/8″ x 3-1/4″). Connect the telephone audio loop between the Firefighters ADT-FPJ and ACC-FFT as detailed in the following table and illustration below. To make a call to the main panel, insert the handset plug into the FPJ phone jack. When the call is complete, remove the handset from the jack.
The ACC-FFT Fire Fighter Telephone Module has the capability of annunciating up to 24 FPJ locations or zones when the ACC-25/50ZST is use with an MS-9600, MS-9600LS, MS-9200UD, or MS-9200UDLS Fire Alarm Control Panel. In order to accomplish this, an addressable monitor module, such as the MMF-300 or MMF-301 must be connect to each FPJ-F or group of FPJs to annunciate as illustrated below.